ALL >> General >> View Article
Total Articles: 27
Ventilation system might consist of a wall-mounted Hartzell propeller fan coupled with an automatic shutter or an inlet weatherhood and a control system to activate the fan motor. For rooftop installations, a powered Hartzell hooded roof ventilator, which may contain a motorized shutter, can be used successfully. These systems would provide make-up air mainly for ventilation purposes.
Practically all air removed from a building is replaced by outside air at the same rate. Outside air will enter by any means available, when the inside air pressure is less than outside air pressure. This happens when exhaust exceeds supply systems capacity to replenish the building envelope with air. Possible consequences of this negative pressure differential are degraded exhaust system performance, loss of environmental control, adverse safety and performance effects on appliances which combust fuel and processes which vent gaseous products via natural draft, increased building structural loads, and excessive forces on exterior doors. Unfortunately, these problems occur where an inadequate amount of replacement or make-up air has been provided. A good make-up air system will alleviate all of these ills by providing the correct amount of replacement air. It may also reduce plant overhead by lowering heating, cooling, and ventilating costs.
In many areas, air must be conditioned before entering a facility. This necessitates that the make-up air system have heating and often air cooling and filtering abilities. A so called make-up air unit is required. Typically a make-up air system includes an air mover section, usually a propeller or centrifugal type fan, an air tempering section containing heating and where necessary cooling and filtering equipment, and a control system.
Fan selection and power requirements are generally determined by the application. When only general ventilation is required (fan pressure requirements are low), a propeller type fan can be utilized. To supply make up air through a duct system with a resistance of 0.5 in w.g. or more, a centrifugal fan should be considered. In either system, diffusers may be used to direct the discharge air velocity.
In situations where the inside air quality is acceptable, often a portion of the inside air may be drawn back through the make-up air unit where it is recirculated back into the building. Advantages of using Hartzell Recirculating Make-Up Air units are lowered heating costs, better indoor air mixing (reduced air stratification), as well as constant building pressurization.
In summary, an adequate amount of makeup air is required for personnel, machines, and processes to operate properly, efficiently, and safely. Failure to provide adequate make-up air is often the cause of unnecessary expenditures for additional exhaust systems and heating or cooling equipment. These devices in turn compound the problem of air starvation within the building. Reliable, cost effective equipment is available from Industrial Pressure Blower Co. to supply the make-up air necessary to balance air removed from a structure.
For additional information please refer to http://industrialpressureblower.com/blower.html
Industrial Pressure Blower Co.
General Articles1. Private Physiotherapy Clinics In Faridabad
Author: Shalini Arora
2. Diwali - Festival Of Goodness
3. Cabernet Sauvignon 2014
4. Cakebread 2013
5. Excel Family Dental - Who Can Benefit From Orthodontics?
Author: Heidi Huang
6. Skin Rejuvenation
7. Code Garage Tech - Benefits Of Search Engine Optimization (seo) For A Beginner
Author: Code Garage Tech
8. Chinese Magnesium Oxide Industry Has Made Rapid Progress
Author: hu Allen
9. Roofing Services In Charlotte
Author: Lakeside R&R
10. Why Forum Posting Important In Seo
11. Learning Is Power With Raid Data Recovery
Author: Sandra White
12. Selling On Amazon Part - I
13. Quality Private-label Softgels
14. Anti-discrimination Chief Part - Ii
15. Sealants And Tools Offers General Purpose Silicone Sealants
Author: Chad Lakin