ALL >> General >> View Article
Fan Blower Performance Curves
Total Articles: 50
Fan performance curves are actually composed of four separate curves:
• Static Pressure vs. Volume Curve: This plot is the one often referred to as the "fan curve" or "characteristic curve" because it defines all the possible pressure-volume combinations the fan is capable of producing given stated conditions (i.e. rpm and gas density). Note that this curve has two regions - one marked by dashed lines and the other by a solid line. Fans must be selected so that the design point is located on a solid portion of the curve, preferably in an area of high operating efficiency. Operation on the dashed portion of the curve should be avoided as it is a zone of potentially unstable performance. For this reason it is wise to allow some reserve between the peak static pressure and the design pressure to compensate for a higher resistance to flow than anticipated by the design calculation.
• Static Efficiency vs. Volume Curve: In most instances it is desirable to have a fan perform as close to its peak efficiency as possible. The static efficiency vs. volume curve illustrates the efficiency of fan performance at a glance.
• Power vs. Volume Curve: This plot illustrates the power draw of the fan for any point on the characteristic curve.
• System Curve: The system curve defines the volume flow rate versus pressure characteristics of the system in which a fan will be installed.
The fan curve is a graphic presentation of fan performance. It is one of the most useful tools available during the fan selection process. While multi-rating tables are convenient (see page 12), performance curves offer additional information such as - how much reserve pressure head exists between the design pressure and the peak static pressure, the maximum power the fan might draw, and the efficiency of operation.
For most applications, the volume flow rate to pressure relationship is governed by the following equation, often called the "duct law":
Once the system designer has determined the system pressure loss (P) for one flow rate (CFM), it is very easy to calculate the corresponding pressure loss for any other flow rate using this "law". The system curve is not included on the performance curve when it is issued from the fan manufacturer and its determination is left to the system designer.
At this juncture it is prudent to reiterate that a fan running at a particular speed can have an infinite number of operating points all along its characteristic curve. The fan will interact with the system to produce an operating point at the intersection of the system curve and the fan curve. Note that it is the system in which the fan is installed that will determine the operating point on the fan curve. Thus it is vitally important that the system designer accurately determine the system losses in order to ensure that the actual air flow rate is as close as possible to the design air flow rate.
For additional information please refer to http://cbblower.com/fanblower.html
Industrial Process Equipment Designer
CB Blower Co.
General Articles1. Why Eye Creams Are Important
2. Preparing For Usa Basketball Tours Understanding The Organisations And Categories
Author: Brett Rainbow
3. Ipad Vs Smartphone Who Will Win The Experience Battle?
Author: Patrik Murphy
4. Avail The Service Of Radius Moving For Best Moving Experience
5. Hermal Mass Flow Meters - Finding A Value In Many Industries
6. A New Example For Cyber Threat Hunting
Author: Bradon Wilson
7. What To Do If Windows Is Unable To Run The Software Protection Service On A Local Computer.
Author: Bradon Wilson
8. The Hidden, Emotional Effects Of Acne
Author: Rahul Sharma
9. Importance Of Prescribed Supplements For Your Healthy Growth
10. How Can I Invest In Cryptocurrency ?
11. Pharmasynth Offers Best Pcd Pharma Franchisee Opportunities For Business Partners
12. Ich Liebe Die Tatsache, Dass Es Zwei Kleider In Einem Geben Kann
13. Celebrate Your Partner’s Birthday By Sending A Stunning Flower Box
Author: Carl Glendon
14. What Happens During A Recession?
15. Important Gold Trading Tips For Beginners