ALL >> Others >> View Article
Blowers Performance Curve
Total Articles: 25
While multi-rating tables are convenient, fan performance curves offer additional information such as - how much reserve pressure head exists between the design pressure and the peak static pressure, the maximum power the fan might draw, and the efficiency of operation.
Fan curves are based on laboratory test data and are sometimes referred to as "test curves". A typical test curve will often define the performance parameters for a specific design and size of fan, operating at a given speed, moving a gas of a given density. Inspection of this graph will show that it is actually composed of four separate curves:
• Static Pressure vs. Volume Curve: This plot is the one often referred to as the "fan curve" or "characteristic curve" because it defines all the possible pressure-volume combinations the fan is capable of producing given stated conditions (i.e. rpm and gas density). Note that this curve has two regions - one marked by dashed lines and the other by a solid line. Fans must be selected so that the design point is located on a solid portion of the curve, preferably in an area of high operating efficiency. Operation on the dashed portion of the curve should be avoided as it is a zone of potentially unstable performance. For this reason it is wise to allow some reserve between the peak static pressure and the design pressure to compensate for a higher resistance to flow than anticipated by the design calculation.
• Static Efficiency vs. Volume Curve: In most instances it is desirable to have a fan perform as close to its peak efficiency as possible. The static efficiency vs. volume curve illustrates the efficiency of fan performance at a glance.
• Power vs. Volume Curve: This plot illustrates the power draw of the fan for any point on the characteristic curve.
• System Curve: The system curve defines the volume flow rate versus pressure characteristics of the system in which a fan will be installed.
For most applications, the volume flow rate to pressure relationship is governed by the following equation, often called the "duct law":
Once the system designer has determined the system pressure loss (P) for one flow rate (CFM), it is very easy to calculate the corresponding pressure loss for any other flow rate using this "law". The system curve is not included on the performance curve when it is issued from the fan manufacturer and its determination is left to the system designer.
For additional information please refer to http://www.northernindustrialsupplycompany.com/burlington/request5.html
Industrial Ventilating Designer
Northern Fan Co.
Others Articles1. Get The Best Protective Packaging Materials Suppliers Dubai
2. Affordable Moving Truck On Rent
Author: Manoj Kumar
3. The Best Replacement Parts For Your Iphone 4s
Author: Darren Chappel
4. Heavy Duty Shelving System That Helps You Maximise Storage Capacity
Author: Abazar Shelving
5. Expats Move To Hong Kong For An Exquisite Experience
Author: jaya dixit
6. 7 Questions To Consider Before You Buy Used Kitchen Equipment
Author: Joseph Rubino
7. Use Ball Pens For Your Business Promotional Purposes
Author: Vijay Singh
8. Elliott Kronenfeld Unveils Secrets To Better Connections In Couples By Intention: Creating And Culti
9. Pandits For Marriage In Bangalore-hindu Traditional Marriage
Author: Online purohtihs
10. Agarwal Packers And Movers Feedback
Author: Neha Gupta
11. Before Buying Wholesale Electronic Cigarettes, Pick The Best Option For You
Author: Ben Oesterling
12. Latest National News - Trends Which Will Put Pedal To Metal
Author: Hannah Smith
13. Where To Find The Best Ar Parts
Author: Scott Rollf
14. Cidc To Award Vishwakarma Award To Mr. Akhilesh Srivastava
Author: Ramya Anumolu
15. Why Would I Need A Commercial Drain Snake?
Author: Lori Troyer