ALL >> Others >> View Article
Blowers Performance Curve
Total Articles: 25
While multi-rating tables are convenient, fan performance curves offer additional information such as - how much reserve pressure head exists between the design pressure and the peak static pressure, the maximum power the fan might draw, and the efficiency of operation.
Fan curves are based on laboratory test data and are sometimes referred to as "test curves". A typical test curve will often define the performance parameters for a specific design and size of fan, operating at a given speed, moving a gas of a given density. Inspection of this graph will show that it is actually composed of four separate curves:
• Static Pressure vs. Volume Curve: This plot is the one often referred to as the "fan curve" or "characteristic curve" because it defines all the possible pressure-volume combinations the fan is capable of producing given stated conditions (i.e. rpm and gas density). Note that this curve has two regions - one marked by dashed lines and the other by a solid line. Fans must be selected so that the design point is located on a solid portion of the curve, preferably in an area of high operating efficiency. Operation on the dashed portion of the curve should be avoided as it is a zone of potentially unstable performance. For this reason it is wise to allow some reserve between the peak static pressure and the design pressure to compensate for a higher resistance to flow than anticipated by the design calculation.
• Static Efficiency vs. Volume Curve: In most instances it is desirable to have a fan perform as close to its peak efficiency as possible. The static efficiency vs. volume curve illustrates the efficiency of fan performance at a glance.
• Power vs. Volume Curve: This plot illustrates the power draw of the fan for any point on the characteristic curve.
• System Curve: The system curve defines the volume flow rate versus pressure characteristics of the system in which a fan will be installed.
For most applications, the volume flow rate to pressure relationship is governed by the following equation, often called the "duct law":
Once the system designer has determined the system pressure loss (P) for one flow rate (CFM), it is very easy to calculate the corresponding pressure loss for any other flow rate using this "law". The system curve is not included on the performance curve when it is issued from the fan manufacturer and its determination is left to the system designer.
For additional information please refer to http://www.northernindustrialsupplycompany.com/burlington/request5.html
Industrial Ventilating Designer
Northern Fan Co.
Others Articles1. Famous Tamil Trinities
Author: Rahul Mehta
2. Why Mom Says No To Most Of Your Bad Habits
Author: Louie O'Connor
3. Sensational Journey Awaits One Call Ahead
Author: Jolin Amandaz
4. Right Mothers Day Flowers Delivery Services In Calgary
Author: Jim Carrey the author of this article.
5. Hotel Service By Ask4rooms
Author: PK bahrti
6. Skills That Successful Photographers Must Possess
Author: Michael Cray
7. The Joy Of Smoking Pipes
8. Title:a Look At Meditation Author
Author: Triguna yoga
9. Shoot It! Share It! Hash Tag It! : Wedding Photo Booth
Author: William is the author of this article.
10. Constructive And Colossal Platform Of Ijar And Ijsr For Global Researchers
Author: John Watson
11. The Complete Jewelry Purchasing Guide
Author: Archana Pandit
12. Ipc Certification Courses In Electronics
Author: Bob Wettermann
13. How To Build Better Skills With Driving Simulators
Author: Eesha Zaveri
14. Tips For Students On How To Become More Confident To Sit For The Exams
Author: Louie O'Connor
15. Budget Friendly Home Security Tips
Author: Edward John