Welcome to 123ArticleOnline.com!
ALL >> Others >> View Article

Blowers Performance Curve

By Author: Oleg Tchetchel
Total Articles: 25

While multi-rating tables are convenient, fan performance curves offer additional information such as - how much reserve pressure head exists between the design pressure and the peak static pressure, the maximum power the fan might draw, and the efficiency of operation.

Fan curves are based on laboratory test data and are sometimes referred to as "test curves". A typical test curve will often define the performance parameters for a specific design and size of fan, operating at a given speed, moving a gas of a given density. Inspection of this graph will show that it is actually composed of four separate curves:

• Static Pressure vs. Volume Curve: This plot is the one often referred to as the "fan curve" or "characteristic curve" because it defines all the possible pressure-volume combinations the fan is capable of producing given stated conditions (i.e. rpm and gas density). Note that this curve has two regions - one marked by dashed lines and the other by a solid line. Fans must be selected so that the design point is located on a solid portion of the curve, preferably in an area of high operating efficiency. Operation on the dashed portion of the curve should be avoided as it is a zone of potentially unstable performance. For this reason it is wise to allow some reserve between the peak static pressure and the design pressure to compensate for a higher resistance to flow than anticipated by the design calculation.

• Static Efficiency vs. Volume Curve: In most instances it is desirable to have a fan perform as close to its peak efficiency as possible. The static efficiency vs. volume curve illustrates the efficiency of fan performance at a glance.

• Power vs. Volume Curve: This plot illustrates the power draw of the fan for any point on the characteristic curve.

• System Curve: The system curve defines the volume flow rate versus pressure characteristics of the system in which a fan will be installed.

For most applications, the volume flow rate to pressure relationship is governed by the following equation, often called the "duct law":

Once the system designer has determined the system pressure loss (P) for one flow rate (CFM), it is very easy to calculate the corresponding pressure loss for any other flow rate using this "law". The system curve is not included on the performance curve when it is issued from the fan manufacturer and its determination is left to the system designer.

For additional information please refer to http://www.northernindustrialsupplycompany.com/burlington/request5.html

Oleg Tchetchel
Industrial Ventilating Designer
airknife@cogeco.ca
Northern Fan Co.
http://www.northernindustrialsupplycompany.com/burlington/request7.html
http://www.northernindustrialsupplycompany.com/burlington/request2.html

Total Views: 117Word Count: 416See All articles From Author

Others Articles

1. Logistics And Supply Chain Management Software
Author: Dhwani Khatri

2. The Accessories You Use In A Bird Cage
Author: alma miller

3. Ivf Treatment - A Ray Of Hope Against Infertility!
Author: Patrick Quinn

4. Simple Steps Which Will Help You Learn Hc Trucks Easily
Author: 1800 Drivers

5. Ice Cream For The Win
Author: Joseph Rubino

6. Placement Consultants In Delhi
Author: VHR Professionals

7. Online Pandit For Namakaran Puja
Author: Online Purohiths

8. Placement Agency In New Delhi
Author: vhr professional services pvt ltd

9. Top 10 Edm Genres
Author: Your Ghost Producers

10. Ngo In Chhattisgarh And Its Mid-day Meal Impact
Author: Akshaya Patra

11. Key Advantages Of Transport Management System
Author: Dhwani Khatri

12. Art That Connects Everyone All Together
Author: William is the author of this article

13. Talk To Best Astrologers On Phone In India
Author: Future Study Online

14. Use Construction Directory To Compare Multiple Vendors For Getting Construction Materials
Author: John Smith

15. Why Should You Hire Professionals For Horizontal Rock Sawing?
Author: Jeff Owler