ALL >> Others >> View Article
Fan Blower Performance Curve
Total Articles: 42
Fan curves are based on laboratory test data and are sometimes referred to as "test curves". A typical test curve will often define the performance parameters for a specific design and size of fan, operating at a given speed, moving a gas of a given density. Inspection of this graph will show that it is actually composed of four separate curves:
• Static Pressure vs. Volume Curve: This plot is the one often referred to as the "fan curve" or "characteristic curve" because it defines all the possible pressure-volume combinations the fan is capable of producing given stated conditions (i.e. rpm and gas density). Note that this curve has two regions - one marked by dashed lines and the other by a solid line. Fans must be selected so that the design point is located on a solid portion of the curve, preferably in an area of high operating efficiency. Operation on the dashed portion of the curve should be avoided as it is a zone of potentially unstable performance. For this reason it is wise to allow some reserve between the peak static pressure and the design pressure to compensate for a higher resistance to flow than anticipated by the design calculation.
• Static Efficiency vs. Volume Curve: In most instances it is desirable to have a fan perform as close to its peak efficiency as possible. The static efficiency vs. volume curve illustrates the efficiency of fan performance at a glance.
• Power vs. Volume Curve: This plot illustrates the power draw of the fan for any point on the characteristic curve.
• System Curve: The system curve defines the volume flow rate versus pressure characteristics of the system in which a fan will be installed.
The fan curve is a graphic presentation of fan performance. It is one of the most useful tools available during the fan selection process. While multi-rating tables are convenient, performance curves offer additional information such as - how much reserve pressure head exists between the design pressure and the peak static pressure, the maximum power the fan might draw, and the efficiency of operation.
For most applications, the volume flow rate to pressure relationship is governed by the following equation, often called the "duct law":
Once the system designer has determined the system pressure loss (P) for one flow rate (CFM), it is very easy to calculate the corresponding pressure loss for any other flow rate using this "law". The system curve is not included on the performance curve when it is issued from the fan manufacturer and its determination is left to the system designer.
At this juncture it is prudent to reiterate that a fan running at a particular speed can have an infinite number of operating points all along its characteristic curve. The fan will interact with the system to produce an operating point at the intersection of the system curve and the fan curve. Note that it is the system in which the fan is installed that will determine the operating point on the fan curve. Thus it is vitally important that the system designer accurately determine the system losses in order to ensure that the actual air flow rate is as close as possible to the design air flow rate.
For additional information please refer to http://www.tenderall.com/blower/index.html
Industrial Equipment Engineer
Tenderall Fan Co.
Others Articles1. Dandruff Treatment | Dandruff Control Treatment In Hyderabad
2. Ios (iphone And Ipad Development)
3. A Barstool For Every Restaurant Aesthetic
Author: Joseph Rubino
4. Marriage Astrologer In India - Kundli Matching For Marriage
Author: Future Study Online
5. Klove Studio-delivering High End Lighting For Home
Author: Klove Studio
6. Choosing Your Perfect Vapor Juice
Author: Gaius Monteyro
7. Reasons Why Online Construction Directories Is Common In Usa?
Author: John Smith
8. 5 Considerations To Make Before Trying To Replace An Ipad 4 Mini Battery Or Other Parts
Author: Darren Chappel
9. Enjoy Premium Airport Transfer Dubai By Availing Al Falasi Services
10. How To Use Spray Foam Insulation Kits
Author: Aaron Abrams
11. 4 Common Sprinkler Problems And The Ways To Get Rid Of Them
Author: Matthew Haiman
12. Important Considerations When Purchasing Ar-15 Parts And Firearms
Author: Scott Rollf
13. Mobile Motherboard Repair
14. Top 3 Apartment Smoke Detectors Types
Author: Matthew Haiman
15. Smart Tips You Must Follow To Select A Reliable Video Accessories Rental Company