ALL >> General >> View Article
How To Increase Ventilator Performance
Total Articles: 42
A fan cannot perform as designed if the air flow surfaces are distorted by contaminants. Even in large fans, a sixteenth of an inch of build up can reduce performance. Centrifugal fans will move some air even when running backwards. While some types would use so much horsepower they would trip circuit breakers, other design s could run for years without being detected. Fan components may be out of position due to routine cleaning or painting or the wheel could have shifted during shipment. For backward inclined fans, the relation of wheel to inlet cone is very critical. Even a quarter of an inch can have a major impact. The fan’s installation and maintenance literature shows the proper positioning of the wheel to the inlet cone.
Industrial processes and plant ventilation systems often need more air than originally designed. Increased production requirements, process changes, and facility renovations are a few of the major reasons. Additionally, the lack of adequate maintenance over time can negatively impact system airflows. This article discusses several procedures that can increase airflow. Often airflow can be increased by adhering to proper fan maintenance procedures as outlined in fan installation and maintenance literature.
The design and maintenance of the system plays a large role in achieving the overall desired performance. Visual inspections often reveal some easily rectified problems that can significantly impair performance. If the system has not been properly maintained, clogged filters or obstructed coils will reduce airflow. The greater the obstruction, the greater the loss in airflow. Any leaks in the ductwork will contribute to reduced perfo rmance, especially leaks around plenum bulkheads that can lead to recirculation of air. Worn flexible connectors are a common source of leaks and should be inspected regularly. If the damper linkage is out of adjustment, the damper may not be opening completely, thereby reducing performance. If inlet dampers are used, make sure they are installed so that the air is pre-spun in the same direction as wheel rotation. For all dampers, make sure there is sufficient clearance for the blades to open and close completely without hitting the ductwork or other system components. Last, for systems with either pneumatic or electric controls, make sure damper actuators are operating properly. Sharp changes in the direction of airflow at either the fan inlet or outlet will disrupt the flow through the fan and impair performance. If it is impossible to straighten the ductwork entering and leaving the fan, the use of inlet boxes and turning vanes can minimize performance losses.
One of the easiest solutions to low airflow problems is speeding up the fan. While airflow is increased by speeding up the fan, so too are static pressure, noise, and power requirements. Therefore, while increasing the fan’s speed is an easy procedure with low first cost, the additional operating expense over time makes it the most costly solution. When increasing fan speed, it is necessary to check the maximum safe speed of the fan and make sure the motor is capable of the horsepower required to run the fan at the new speed. But never run a fan beyond its maximum safe speed.
On a first-cost basis, adding or replacing fan equipment is the most costly alternative. However, on a life-cycle-cost basis, considering operating and maintenance expense, it can be the least expensive, as compared to increasing the speed of an existing fan. Sometimes a second fan may be added, either in series or parallel with the original, although it may be more cost effective to simply upgrade the system with a new fan capable of the required airflow and pressure. Adding another fan in series will increase the airflow because of the additional pressure. The operating point of the new system moves further out/up the system curve. Where duct size is adequate to handle the desired amount of air but the existing fan doesn’t provide sufficient pressure, a second fan in series may be the best solution. However, make sure the ductwork can handle the increase in pressure. Adding another fan in parallel with the first will increase airflow due to the combined capacities. Because capacities are being combined instead of pressures, a greater increase in airflow will result for a given system. However, system pressures will also increase and caution is required to avoid the unstable operating area of the combined fan system.
When more air is required it is important to investigate the system on a step-by-step basis, considering the least expensive possibilities first. For existing systems that seem to have lost performance, fan and system maintenance is the place to start. Often, simply improving the efficiency of existing components will suffice. For systems that require greater airflow and / or pressure, increased fan speed is generally the first alternative. However, when large increases in performance are required, there may be no alternative but to purchase a larger fan.
Additional information can be found at the Tenderall Fan company web site http://www.tenderall.com/ahu/index.html
Air Systems Engineer
Tenderall Fan Co.
General Articles1. Best Women Styles In Coats
2. Data Loss Prevention – What Is It?
Author: Daniel Gachara
3. An Overview Of Mcse Windows Server 2012 Training
4. As Fiduciary Concerns Grow, Multiple Employer Plans Look Compelling To Some Companies
Author: Terrance Power
5. Learn Photography With Some New Strategies
Author: Ajay Chauhan
6. Ram Nath Kovind Gets Votes Worth 60683, Meira Kumar 22941 In First 4 States
Author: new indian express
7. Ensure World-class Quality & Productivity To Your Textile Manufacturing Processes With A.t.e’s Broad
Author: K V Gopalakrishnan
8. Probe Into Murky Prison Affairs Gets Under Way
Author: new indian express
9. Presidential Poll Results Live Updates | Counting Underway; Ram Nath Kovind Gets 60,683 Votes In Fou
Author: new indian express
10. What Defines A Luxury Home?
Author: The Cheesy Animation
11. A Quick Glimpse On The Best Waterproof Speaker: Speakstick On The Go!
Author: Rioven Schmidt
12. Benjamin, Chaise & Associates-debt Collection Myths
13. Cheap Price Halong Cruise – A Private Asia Tour Must Include This Type Of Option!
Author: Nguyen Xuyen
14. Getting Started With Android Auto And Your Subaru Liberty
Author: Ben Sporn
15. Learn About The Most Precious Online Assistance For Your Business Development
Author: Louis Harris