ALL >> Automobiles >> View Article
Combustion Fan Blowers
Total Articles: 55
The amount of air required for theoretically perfect combustion is based on the portion of the combustible substances carbon (C), hydrogen (H2), oxygen (O2), and sulfur (S) contained in fuel. These are the only combustibles found in common fuels. In practice, the combustion system designer should determine the actual air volume requirements and the excess air margin based on an analysis of the fuel in question. The fan selection for the application should be capable of meeting both conditions with good efficiency, economy, and stability. Whenever possible, the actual condition should represent the most efficient point of operation for the fan selected for the application.
The combustion of coal and most fuel oils will release sulfur fumes into the flue gas. If a wet scrubbing or cleaning apparatus is used, water vapor will combine with the sulfur to form sulfuric acid. This can place severe constraints on the fan types available to handle this highly corrosive gas stream. For this very reason, flue-gas-desulfurization equipment is designed into the pollution control systems of many combustion processes. Another alternative to reduce the potential for sulfuric acid in the exhaust system is to mix lime or crushed limestone in a fluidized bed combustion process so the lime will neutralize the sulfur and stabilize the pH of the exhaust gases.
Ideally, the fan in any combustion process will supply just enough air to completely burn all the fuel, and no more. This will help keep heated, but unused, air from going up the stack. Actually, this idea is approachable with gas burners but impractical with wood- or coal-fired combustion. Thus, nearly all air volume requirements for combustion processes are calculated to include some margin of excess air. Insufficient air volume will result in wasted fuel and excessive particulate along with potentially explosive gases in the exhaust system. From this viewpoint it is better to include excess air volume.
To reduce volume and pressure to meet the actual design or reduced load conditions, inlet dampers or variable frequency drives are used. Variable speed offers the most efficient means of performance reduction, although the initial cost and equipment maintenance is greater than that of dampers. These must be evaluated on an individual job basis to determine whether the power savings will offset the greater initial price differential and added maintenance costs. The criteria for selecting the fan motor is usually specified per job. Often, the motor is sized to handle the hot operating conditions so the fan can be dampered for low load periods such as start-up or shut-down. This reduces the dampering, or turndown, range required under actual conditions.
Fans used in combustion processes, whether forced or induced draft, should be capable of meeting the following minimum requirements:
1) The fan pressure curves should be stable throughout the entire operating range of the system. Certain fans, such as most radials, pressure blowers, and airfoil fns, are stable from wide-open to completely closed-off to offer the broadest possible control range.
2) The fan and all its components should be designed to meet even the test block condition without passing through the first critical frequency of the rotating parts. A common specification calls for the fan shaft’s first critical speed to be 125% of the maximum operating speed.
3) The entire fan assembly should be rugged to withstand industrial service. Catalogs or drawings should contain complete material specifications.
4) Whenever possible the entire fan, motor, and drive assembly should be factory assembled, aligned, and test run to ensure smooth operation. The fan manufacturer should be capable of test running complete assemblies.
Induced-draft fans have further special requirements:
5) Where fan airstream temperature exceeds 300°F., the fan should include a shaft cooler and the bearing base should be separated from the fan housing.
6) The fan should be selected to handle the maximum particulate loading. Radial, radial-tip, and backwardly inclined designs in a variety of alloys are suitable to handle a wide range of contaminated airstreams.
7) Fans handling particulate-laden airstreams should be furnished with shaft seals to protect the inboard bearings. Ceramic-felt shaft seals usually provide the best protection in these applications.
8) Fans fao dirty airstreams should also be furnished with a cleanout door and a drain to facilitate periodic cleaning. Various quick-opening, bolted, and raised, bolted cleanout doors and drain connections are generally available.
9) Blade liners, housing liners, and hard surfacing of blades and/or inlet cones may be desirable, depending on the particulate loading.
Additional information can be found at the Canadian Blower company web site http://www.canadianblower.com/fans/index.html
Canadian Process Air Systems Designer
Automobiles Articles1. Important Things To Keep In Mind When Your Car Breaks Down
Author: Paul Zervos
2. E-rickshaws Are The Perfect Way To Keep Your City Green.
Author: Power Electric Vehicle
3. The Audi Car Dealers Miami Offer Certified Pre Owned Cars In Competitive Price
4. Top Three Reasons To Consider Outsourcing Your Cad Project
Author: Top Three Reasons To Consider Outsourcing Your CAD
5. For An Updated Speed — the Cummins’ Compound Turbo Way
Author: Rip Rook
6. Customized Harley Davidson With Actual Parts Is The Ultimate Style
Author: Levi Fysh
7. Commercial Kitchen Equipment Dubai
Author: AL RAZANA KITCHEN
8. An Overview About 3d Cad Modeling, Plm And Pdm
Author: An Overview About 3D CAD Modeling, PLM and PDM
9. Relax And Rove With Private Driver And Car Services
Author: Toby Pratt
10. 7 Things You Need To Know Before Buying A Car Battery Charger
Author: Michael Foley
11. What Is The Best Time To Trade-in Your Old Car?
Author: Wiliams Orchard
12. The Brilliance Of Japanese Cars Imported From Japan
13. New & Upcoming Sedan Cars In India 2017
Author: Trending Car
14. Compelling Reasons To Fixing Car Dents With Paintless Dent Repair
Author: Gordon Coubrough
15. Choosing Limo Service Fort Worth