ALL >> Business >> View Article
Instructions To Install Air Conditioner Wall Split
Total Articles: 1
The article show you the general instructions to install air conditioner wall split
EditMethod 1 of 3: Install the Indoor Unit
1Select an unobstructed location on your interior wall to mount the indoor air conditioning unit.
Avoid direct sunlight and heat sources.
Avoid locations where gas may leak or where oil mist or sulphur exists.
The indoor unit requires at least 6" (15 cm) of open space surrounding its top and sides. The unit should also be mounted at least 7 feet (2.13 m) above the ground.
Install the unit at least 3.3 feet (1 m) away from antenna, power or connecting lines that are used for television, radio, home security systems, intercoms or telephones. The electrical noise from these sources could cause operational problems for your air conditioner.
The wall should be strong enough to hold the unit's weight. You may need to construct a wood or metal frame to provide added support.
2Secure the mounting plate to the interior wall.
Hold the mounting plate against the wall where you want to install the indoor unit.
Use a level to make sure the plate is both horizontally and vertically square.
Drill holes into the wall at the appropriate spots to affix the plate to the wall.
Insert plastic anchors into the holes. Secure the plate to the wall with tapping screws.
3Create a hole in the wall to fit the piping.
Find the best spot for the hole to the exterior based on the opening in the mounting bracket. You should also consider the length of the pipe and the distance that it needs to travel to reach the outside unit.
Drill a hole that is 3" (7.5 cm) in diameter through the wall. The hole should slope downward toward the exterior to ensure adequate drainage.
Insert a flexible flange into the hole.
4Check the electrical connections.
Lift the unit’s front panel and remove the cover.
Be sure the cable wires are connected to the screw terminals. Also, make sure that they match the diagram that comes with the unit.
5Connect the pipes.
Run the piping from the indoor unit toward the hole drilled through the wall. Minimize bending to ensure that the unit performs well.
Cut a length of PVC pipe 1/4" (6 millimeters) shorter than the length between your interior and exterior wall surfaces.
Place the pipe cap on the interior end of the PVC pipe. Insert the pipe into the hole in the wall.
Bind the copper pipes, the power cables and the drain pipe together with electrical tape. Place the drain pipe on the bottom to ensure a free flow of water.
Secure the pipe to the indoor unit. Use 2 wrenches, working in opposite directions, to tighten the connection.
Join the water drainage pipe to the indoor unit’s base.
Run the bound pipes and cables through the hole in the wall. Make sure that the drainage pipe allows water to drain in an appropriate place.
6Secure the indoor unit to the mounting plate by pressing the unit against the mounting plate.
EditMethod 2 of 3: Install the Outdoor Condenser
1Choose the best place to install the outdoor unit.
The outdoor unit’s location needs to be away from any heavily trafficked, dusty or hot areas.
The outdoor unit needs 12" of space surrounding its perimeter to ensure proper functioning.
2Lay the concrete pad on the ground and make sure that it is level. The pad should be high enough so that the condenser will sit above the level of winter snows.
Set the outdoor condenser on top of the pad. Use rubber cushioning under the unit's feet to minimize vibration.
Make sure that no antenna of a radio or television is within 10 feet (3 meters) of the outdoor condenser.
3Connect the electrical wires.
Remove the cover.
Refer to the unit’s wiring diagram and make sure the cable wires are connected as the diagram suggests. Following the manufacturer's instructions for wiring is crucial.
Fasten the cables with a cable clamp and replace the cover.
4Secure the pipes’ flare nuts to the corresponding pipes on the outdoor unit.
EditMethod 3 of 3: Complete the Split System Air Conditioner Installation
1Bleed the air and humidity from the refrigerant circuit.
Remove the caps from the 2-way and 3-way valves and from the service port.
Connect a vacuum pump hose to the service port.
Turn the vacuum on until it reaches an absolute vacuum of 10mm Hg.
Close the low pressure knob and then turn off the vacuum.
Test all of the valves and joints for leaks.
Disconnect the vacuum. Replace the service port and caps.
2Wrap the joints of the piping with insulating covering and insulating tape.
3Affix the piping to the wall with clamps.
4Seal up the hole in the wall using expanding polyurethane foam.
This article was writen by Air conditioner bracket
Business Articles1. Why Indian Crafts Is A Best Company To Buy Furniture Online ?
Author: Mukesh Tiwari
2. How Does Digital Marketing Works? And What Is Importance Of Digital Marketing?
Author: MBHITECH Solutions
3. What To Know More About Outsourcing Accounting Services?
4. How To Manage The Accounting Service For Your Business?
5. Thermal Fluid Heat Transfer Systems
6. Employee Provident Fund, Labour Law, Employees State Insurance Consultant In Mumbai
Author: ATSCO Corporation
7. Top Mba Colleges In Jaipur
8. Android App Development Company In Usa, Android App Development Web Services, Android App Developmen
9. The Case For Growth Of Car Parking Tensile Structure In India
Author: Tensile Structure
10. Photocopier, Currency Counting Machines And Cctv Service Provider In Mumbai
Author: Amtech Enterprises
11. Why Opt For Custom Shipping Crates?
Author: Kurt Heimbrock
12. למעלה קבלני חיתוך בטון
13. Pain Management Doctors In San Antonio Texas
14. Regular Professional Mold Inspections Ottawa – Why Every Homeowner Should Consider
Author: Mark Simon
15. Online Class Help, My Online Class Help