ALL >> Business >> View Article
High Pressure Regenerative Blower
Total Articles: 25
High pressure channel blowers are oilless and have no complicated intake / exhaust valving. Most can be mounted in any plane and, with dynamically balanced impellers, generate little vibration. Because they are nonpositive displacement compressor/vacuum pumps, they discharge air that is clean and pulsation free, which are important considerations for today's plant instruments and controls.
Regenerative blowers operate as a multistaged compressors. Each blade-to-blade regeneration stage results in a slight pressure increase. Total pressure rise from air entry to discharge yields a continuous operating pressure up to 300-in. w.g. (11 PSIg) or a vacuum to 14-in. Hg with continuous flows to more than 1400 scfm (Fig. 3).
Regenerative blowers are ideal for moving large volumes of air at low pressures or vacuums. Unlike positive displacement compressors and vacuum pumps, they pressurize air through a nonpositive displacement method. Typical regenerative blower applications include sewage aeration, vacuum lifting, vacuum packaging, pneumatic conveying, concrete aeration, pond aeration, vacuum tables, drying, dust/smoke removal, air sparging, and chip removal.
Of all air handling equipment, regenerative blowers are probably the least understood. However, when system parameters fall within their range, they can be among the most cost-effective methods for moving air and producing pressure or vacuum.
Regenerative blowers are sometimes called side channel blowers or ring compressors, terms that refer to their physical construction. They can be direct or belt driven. In direct drives, the impeller is mounted on an electric motor shaft. The number, size, and angle of the blades on the impeller determine pneumatic performance as well as the relationship between the impeller and housing. Some blowers have rather flat performance curves while others have steep ones.
The impeller spins within a housing with an inboard and outboard channel. It is from this configuration that the name side channel blower is drawn. As the impeller blades pass the inlet port, they draw air in. The impeller rotation pushes air outward and forward into the channels. The air then returns to the base of the blade. As the impeller spins, the process repeats. This regeneration gives the blower its pressure/vacuum capabilities.
Most blowers are single stage: Air travels around the blower housing once and is discharged. Two-stage regenerative blowers can provide almost twice the pressure or vacuum of single-stage units. In a single-impeller, two-stage unit, air makes one revolution around the front side of the impeller. Then, instead of being discharged, the air is channeled to the backside of the impeller through internal porting. Air then makes another revolution around the backside of the impeller before it is discharged. Other two-stage configurations are also available, including designs that use two separate impellers in one housing or two impellers and housings.
Among the major benefits of a regenerative blower is its lack of maintenance and monitoring requirements. The impeller is the only moving part and is wear free and does not come in contact with the housing channels. Self-lubricated bearings are the only parts that wear.
The majority of blower failures are caused by improper installation or operation. Regenerative blowers have close internal clearances between the impeller and housing. It is important to prevent foreign material from entering that space. Ingested debris wedging between the impeller and housing can cause the blower to lock up and lead to a catastrophic failure. A blower should always be equipped with an intake filter. A 10-micron size is usually adequate. Filters must be kept clean. A blocked filter will starve flow.
Overpressurization can also cause deadheading (zero airflow through the blower) and catastrophic failure. Some blowers tolerate deadheading, but other models (typically those above 1 hp) must have air passing through them for cooling. If air does not pass through the blower, heat builds up in the impeller causing it to expand at a faster rate than the housing. Eventually the impeller locks up with the housing and the blower fails. A relief valve prevents overpressurization and deadheading conditions and allows air to pass through the blower.
For additional information please refer to Canada Fan web site http://www.cincinnatifan.net/pressureblower.html
Ventilation Equipment Engineer
Canada Fan Co.
Business Articles1. Finding The Right Camera Bag Could Be Easy With The Discussed Tips
2. Contact The Right Audience And Executives With Pharmaceutical Companies Mailing List
Author: Jane Cannon
3. Understanding The Relevance Of Real Estate Services In 2018
Author: James Hopkins
4. Get Access To Highly Focused Quickbooks Users Email List
Author: Andrew Rayel
5. What Happiness Means To You- Certified Quantum Suc
Author: Christy Whitman
6. Some Very Basic Tricks To Get Your Accounting Right
7. Accounting Service For A Small Business Confirm A Smooth Running
8. Injured By A Drunk Driver Here’s What To Do
9. You Have To Visit The Bank's Site On The Web And Fill In The Application
Author: Brandon Jones
10. Bed Bug Treatment That's Effective And Affordable
Author: Steve Stein
11. Here Are 5 Tips That Will Keep
12. Here’s All That Your Angry Customers Want Your Business To Learn!
Author: Surabhi Joshi
13. Plastic Model Aircraft
14. An Ultimate Guide To Chlorinated Polyethylene And Its Properties
15. Schramsberg Blanc De Blancs 2012